120/208/240 Volt 50 VA Plate or Panel Mounted Transformer with 9 in. lead wires and metal end bells(
Quantity in Basket: None
Plate or panel mounted 120/208/240 Vac Transformer with 9 in. lead wires and metal end bells.
Provide power to 24 Vac circuits in heating/cooling control systems. Intended for use in systems with predictable, uniform loads. Can be used in any application that does not exceed the listed ratings.
Rated at 50 VA.
Color-coded leadwires for primary connections and screw terminals for secondary connections, fixed 1/4 inch (6 mm) male quick-connects or color-coded leadwires for both primary and secondary, are standard. Meet NEC Class 2 requirements.
Meet Underwriters Laboratories Inc. Standard UL 1585 and are identified. Class 2 not wet, Class 3 wet.
Electrical Ratings -Primary Voltage 120 Vac, 208 Vac, 240 Vac .
Electrical Ratings -Secondary Voltage 27.5 V.O.C..
Frequency 60 Hz.
Mounting Includes 1/2 14 NPSM conduit connector and lock nut for mounting on plate or panel (not included) with 7/8 in. knockout, and feet for surface mount.
Electrical Connections (Primary)(in.) 9 in. leadwires.
Electrical Connections (Primary)(mm) 229 mm leadwires.
Electrical Connections (Secondary)(in.) 9 in. leadwires.
Electrical Connections (Secondary)(mm) 229 mm leadwires.
Electrical Ratings -Output 24 Vac at 50 VA.
Dimensions (in.) 3 3/16 in. high x 2 3/16 in. wide x 3 5/8 in. deep.
Dimensions (mm) 81 mm high x 56 mm wide x 93 mm deep.
Temperature Ratings (F) -20 F to +105 F.
Temperature Ratings (C) -29 C to +41 C.
Approvals, Underwriters Laboratories Inc UL Listed: File no. E14881, Guide no. XOKV..
Approvals, Canadian Standards Association Certified: File No. LR95329-18.
Includes Button for manually resetting the circuit breaker and metal end bells..
Tradeline Value Tradeline.
Replaces Part Numbers:65F1601, 65F16, 65G4601, 65G46, AT150F1022, CARAT150F1022
Used In Equipment Model Numbers: